for Grove City, OH
Outstanding experience in a world of gray!
Gregory - Grove City, OH
The gentleman was very personable, wasted no time arriving and wasted no time finding a solution for our AC situation. Definitely a pro- and very fair priced too! HIGHLY RECOMMEND THIS COMPANY!
Very good service
Patricia - Grove City, OH
Polite, informative young man
Christie - Grove City, OH
Noah does a great job and we’re happy to have him do our maintenance.
Chris - Grove City, OH
Very knowledgeable and responsive...came same day and fixed my a/c in 20 minutes...excellent customer service
Great service, Noah was very helpful.
Sam - Grove City, OH
Knowledgeable and friendly service
Rebecca - Grove City, OH
Prompt, polite, good value
Cheryl - Grove City, OH
Great all around service and value
Great Service Technician!
Tony - Grove City, OH
Chad was extremely professional and thorough in his inspection.
Richard - Grove City, OH
The technician was very courteous and respectful to my property. He did a good job of explaining what he found and what needed and did not need to be done.
Michelle - Grove City, OH
Came out the same day I called and had the parts to fix my A/C!
Foundt he 2006 Bryant heat pump board sending voltage to W, bad defrost board. Removed heat command capability from outdoor unit, (w wire to furnace board). I confirmed thermostat settings, set compressor lockout to 40 from 35. Added Auto Mode for customer control.
Pilot not lit. Cleaned pilot orifice and thermocouple. Re-lit pilot after visual inspection, confirmed that flame failure will turn off baso switch, checked controls. Found bad thermostat, jumped and confirmed furnace operation, replaced thermostat, now heating, confirmed no CO spilling, furnace is still super old, alerted customer.