for Reynoldsburg, OH
I completed a return service and found that the drain line was clogged, I unclogged and cycled the units. Everything is now operating as intended.
Upon arrival went over options with customer for replacing entire units. Customer will follow-up with us the following day.
I completed a return service for a Carrier 13 SEER 2.5 Ton Air Conditioner. I determined that there was an airflow issue and will be returning to replace unit following week.
I completed a diagnostic service call on a Bryant air conditioner. I determined that the breaker panel connection was loose. I tightened. I found the wire charred and burnt. I corrected wiring. I lastly found insulation bubbled up, I corrected the insulation. System cooling properly upon departure.