for Powell, OH
Client requested an estimate to replace a Lennox gas furnace and air conditioner. I recommend replacing it with a Five Star 80% 45,000 BTU Gas Furnace and a Five Star 13 SEER 2 Ton Air Conditioner. Included in the estimate is a 1 year free service maintenance agreement.
Arrived on site. Met with customer. Made sure a call for heat was present at the stat. Used extension ladder to access roof. Found unit with valve on gas line turned off. Opened valve, cleaned burners. And bleed out air in gas lines from gas being turned off. Unit ignited without issue
Found 2010 Lennox AC low on charge. Added 2 lbs Refrigerant R-410A Puron to system. Customer declined leak search at this time. Leak search is needed to find leak and quote to fix leak. Once charged noticed really low suction pressure checked indoor coil completely caked with dog hair. Customer decided to do it himself. System will not run right until that coil is replaced or cleaned.
Diagnostic service call on 2002 Bryant gas furnace, Found pressure switch code. Checked trap trap was clogged but pressure switch tubing was on the wrong port. Cleared trap with bleach and air. All in all system runs very well. Ran system 20 mins to ensure no more issues. All okay.