for Pataskala, OH
I provided an estimate for a new system in garage
checked water damage/rusted pipe in basement. Ductwork is above a finished basement, some part of the ceiling is ceiling grid and other parts are drywall. The supply pipe to the master is sweating and causing The plywood bellow by the window seal to swell. Ductwork is not insulated, needs insulated to fix water leaking but not very much room to insulate
Replaced warranty board and pev valve and system is as quiet as a church mouse. Although customer had some concerns about the way the condenser high voltage was run being spliced in the breaker panel. Pulled breaker panel and immediately found sparks from 30 amp breaker for condenser. Customer very upset with the way it was spliced into the panel. Tried to rerun current wire not going to work all the wire needs repulsed not enough to reach breaker. Got a hold of manager to see if we can schedule to rerun voltage.