for Obetz, OH
upon arrival found oil on the suction line at the condenser. Also found a puddle of oil underneath the suction line. Found the 2020 Carrier system operating at a 22 SH and .9 SC. Weighed in 1.5 lbs of r410a, now running at a 10 SH and 13 SC. Install coordinator schedule leak repair.
Installed new Carrier 13 SEER 2 Ton Air Conditioner