for Obetz, OH
I arrived on site to give the customer on a new air conditioning and furnace system estimate. I recommended the Five Star 80% Gas Furnace and a Five Star 13 SEER Air Conditioner, as they were the most reliable for the measurements of the customers home. The customer will call us back if they decide to go through with the estimate.
Upon arrival customer stated they turned the 2013 trane furnace on but it would not run. Found 3 pin plug for inducer motor not plugged in all the way on the board and not energizing the inducer motor. Released tight wire and plugged inducer pin into the board. Inducer started up and the furnace came on.
Diagnostic service call for 1990 Rheem AC unit not cooling the house. Service work performed: Found indoor unit very dirty, needs new filters Outdoor unit 100% clogged, cleaned thoroughly, suction 72, high superheat but hot in the house. 63 supply temp 80 in the house with almost 70% humidity
upon arrival found oil on the suction line at the condenser. Also found a puddle of oil underneath the suction line. Found the 2020 Carrier system operating at a 22 SH and .9 SC. Weighed in 1.5 lbs of r410a, now running at a 10 SH and 13 SC. Install coordinator schedule leak repair.