for New Albany, OH
Great and prompt service
Jean-Luc - New Albany, OH
Called for a repair service on our humidifier and they were at my house in less than 4 hours. Corey our technician was very courteous and fixed the problem while also explaining the source of the issue.
Brian - New Albany, OH
Great experience and good price!
Murali Paidi - New Albany, OH
Everything went well. Very knowledgeable technician who shared some good tips and was very patient in answering questions! Very satisfied with the service!!
Dale - New Albany, OH
Appreciate the same day service. Technician Mike was very professional.
Queen - New Albany, OH
The repair technician was very polite and on time. Put dust cover on shoes which I appreciate
Loni - New Albany, OH
We are very pleased we chose Pickerington Heating & Cooling. They are always helpful in scheduling and their technicians are courteous, friendly and knowledgeable. We decided to purchase a contract with Pickerington Heating & Cooling to make sure we are covered for any issues that may arise. Would totally recommend them for your heating and cooling needs.
technician on time
Gary - New Albany, OH
Ben Johnson is a plus for the image of your company going forward.
Great service for yearly maintenance
DEBBIE - New Albany, OH
Have used before and always satisfied.
Amazing Service and knowledgeable staff.
Jennifer - New Albany, OH
My overall experience has been excellent with Pickerington Heating and Cooling. Very professional and courteous. They arrived on time and were very friendly and knowledgeable. The two took the time to also explain every question that I had and offer very great advice.
Use them every time for HVAC needs
Leah - New Albany, OH
I am very pleased with the service from Pickerington Heating and Cooling. I highly recommend.
I completed the scheduled maintenance agreement cooling tune up on a Carrier air conditioner. I visually inspected the unit. Checked voltages, amps and pressures. I inspected the evaporator coil. I checked the temperature difference across the coil. Inspected heat pump. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. Cycled and monitored system. All operating normally at this time.