I replaced OEM WARRANTY Bryant Evolution Connex communicating thermostat.
I ran diagnostic performed check on furnace adjusted st stage gas pressure to 1.65, was at 1.8. Cleaned flame sensor. Sytem correctly went into high fire after 20 minutes of running low fire.
Found nest thermostat sending voltage to both heating and cooling equipment bad thermostat. replaced thermostat with one provided with install last winter.
Replaced inducer cap on 2004 Bryant 90% and system fired up no problem. Quoted customer for replacement 90% OEM Inducer Motor.
I replaced an OEM Inducer Motor for a 2006 Comfortmaker gas furnace. Everything running properly at time of departure.
Did not quote replacement as current unit is only 6 years old. Explained to customer I want to work on the furnace and get it running better. Office will schedule a future visit.
Trap not secure. Switch closes at 1.33 and draft is only 1.35 quoted heat exchanger 90% trane.
I installed Carrier 80% 90,000 BTU Gas Furnace
Model # 58SBOA090E171214 CS 3.5T 17"
I installed a new iWave-R Air Cleaner