I completed a diagnostic on a York Electric Furnace. I determined that the top breaker for furnace was bad, furnace was not wired properly and the thermostat needed replaced. I replaced the thermostat and found the contactor not closing
Near Harrison Rd NW, Johnstown,
Found Carrier AC slightly overcharged. Removed .5 pounds of refrigerant. The system is cooling properly.