for Hilliard, OH
I completed a return service to replace the condenser coil, everything is cooling as intended.
I completed a return service to search for a leak on a Carrier air conditioner. I found that the condenser coil had a leak. I went over options with the customer. I will return later in the week to complete.
I performed Spring Tune-up on Carrier Air Conditioner. I visually inspected the unit. Checked voltages, amps and pressures. I inspected the evaporator coil. I checked the temperature difference across the coil. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. Cycled and monitored system. All operating normally at this time.