for Hilliard, OH
Upon arrival found water on basement floor around 2020 Carrier Gas Furnace 96% Variable Speed Two-Stage 60,000 BTU furnace. Opened burner door and found rubber elbow was disconnected from condensate trap inside furnace. Elbow and drain have a coating of oil inside them. Removed both and cleaned oil from parts. Also ruffed the surfaces up on the elbow, drain line and drain trap. Oil is coming from the heat exchanger. Oil is used to make the heat exchanger at the factory. No water leaking at this time. Normal operation
Diagnostic service call on 2003 Trane furnace. Condensation drain line was clogged, due to water softener tubes draining into the condensation line drain, it would overflow and leak down into blower housing, replaced condensation drain line, pulled and cleaned blower housing, furnace operational at departure.
Hilliard heating and cooling service
Diagnostic service call on 2019 Carrier Furnace
Tech returned to replace under warranty limit switch on 2019 Carrier Furnace.
Hilliard heating and cooling weekend service.