for Groveport, OH
Christa - Groveport, OH
They arrived on a Sunday and fixed the issue in 20 minutes!
Found a 80% Bryant gas furnace in the basement. Found the inducer running on the furnace, pressure switch closes but the ignitor wasn’t glowing. Removed plug on ignitor to check ohms across ignitor and found the plug wasn’t pushed all the way in and making a good connection. Found 120v to ignitor. Ignitor ohms are at 62. Plugged ignitor back in and checked for a secure fit.
I am Performing our Five Star Tune-Up & Safety Check on a Gas Furnace. All readings were within manufacturer's specifications, unit operating properly at this time.