for Galloway, OH
Teresa - Galloway, OH
Furnace and Heat Pump Tune Up And Safety Check Air handler is from 1977 ran system in emergency heat all 3 strips came on total amps on system was 62.8. 20 amps for each strip and 2.4 amps for the blower which is good however; if a part were to go bad on this air handler finding parts for this will be very expensive. Heat pump is a 1997 Goodman needs a capacitor it is low on the fan side registered 3.77 out of 5. 4.5 is the allowable for the capacitor. Checked charge charge was 54-256 which is good saturation for r22 system should equal the ambient conditions outside. It did it is 41 degrees outside and saturation was 41. Was able to force defrost at the board. All in all system is running as it should at this time the age is the only concern at this time.
Galloway heating and cooling service