for Canal Winchester, OH
I Replaced the control board and blower on a 2017 Carrier and now runs at full speed. Cleaned condenser coil that was blanketed. While checking the AC charge to verify proper levels the condensing unit blew the fuse at the furnace. Found a chewed up low voltage wire shorting out the system. Repaired wire, changed fuse, and system is operational again.
Customer stated that the 2004 Air Conditioner was not cooling down to 70. Doesn’t line up with her thermometer that does temperature. Adjusted blower speed to get a 15. Currently operating at a 2 ton blower on a 3 ton coil. Checked out r/22