for Canal Winchester, OH
I arrived on site to perform an inspection on a Bryant air conditioning unit. During the inspection I found that the unit had a leak at the manifold. We also found that the coil was bad and needed to be replaced. Unit was not operational at the time of departure.
I completed a return service to replace the drain pan. I cycled and everything is now operating as it should.
Prior to this appointment the customer cancelled their estimate due to an emergency.
I completed a diagnostic service call on an air conditioner. I determined that the unit's evaporator coil needed to be replaced. I went over options with the customer.
I completed a return service to correct the wiring to help fix the customer's airflow issues. Customer's units operating properly.