for Blacklick, OH
Steve P. - Blacklick, OH
Been doing business with Noah and team for a few years now. Young man has a special knack for HVAC systems. He's keeping mine running just fine. Never an upsale and a accurate diagnosis of my issues. I will continue to use them.
Cleaned flame sensor on 2002 Bryant Gas Furnace.
Upon arrival found thermostat set to 74 degrees but house temp is reading 68 degrees. Found furnace tripped on code 13 (Limit circuit lockout) Reset furnace and jumped furnace into high heat. Checked temp rise on high heat, operational at a 55 degree temp rise, Turning off allows blower to run at max heating airflow on low and high heat and also to help out with higher return temps due to bypass humidifier. High heat static pressure is now 1”wc, now have airflow going across heat exchanger to keep prevent overheating.