for Blacklick, OH
Steve P. - Blacklick, OH
Been doing business with Noah and team for a few years now. Young man has a special knack for HVAC systems. He's keeping mine running just fine. Never an upsale and a accurate diagnosis of my issues. I will continue to use them.
Upon arrival found cotton wood on condenser coils, needs cleaned but not completely plugged yet. Tried to clean, hose bib broken on exterior of building. Can not clean at this time. Advised landlord of current issue with hose bib.
Customer stated they are still seeing dark lines on the T6 thermostat. This is the second thermostat since the install. Today customer showed me the dark lines they are seeing. The dark lines are from the digital display board behind the screen of the thermostat. Explained to customer that is normal with this style of thermostat because of how the digital display is recessed inside the front of the thermostat.
Upon arrival for 1998 Trane AC, customer stated the blower inside is not running upon arrival. Found blown 5 amp fuse. Replaced fuse. Cycled ac from thermostat, fuse still didn’t blow. Ac running right now, clean filter, supply air is 56 degrees and return air is 75 degrees. Ac is working at this time. Ac and furnace are both very old. Talked to customer, she wants to get a price on replacement. New furnace going in next week.
I preformed a Real Estate HVAC Inspection. Upon arrival I went through furnace tune up list and confirmed that system is working within manufacture specifications Went through ac tune up list and confirmed that system is working within manufacture specifications Both systems functioning properly upon departure